As per IEC 60947, switchgears with rated voltages up to 1000 V ac and 1500 V dc are termed as low voltage (LV) switchgear.
The term ‘switchgear’ is a generic term encompassing a wide range of products like circuit breakers, switches, switch fuse units, off-load isolators, HRC fuses, contactors, earth leakage circuit breakers (ELCBS), miniature circuit breakers (MCBS), and moulded case circuit breakers (MCCBS), among others.
A commonly followed network combination in LV distribution boards in shown in the figure below.
It is a combination of power control centres and motor control centres or load distribution boards including lighting distribution boards.
The incomer/sub-incomer/ distribution network generally depends on the capacity of the source and the distribution of load centres.
|Conventional Low Voltage Distribution Network|
The characteristics and feature of load controlling and protecting devices vary on the basis of the locations. The system being most commonly followed currently is detailed below.
1. Switching and carrying normal currents (generally above 1200 A);
2. Withstanding abnormal currents for a short duration in order to allow downstream devices to operate;
3. Interrupting the maximum value of the fault current generated in the system;
4. Ensuring the safety to the operating personnel;
5. Inter-locking with downstream equipment; and
6. Facilitating easy maintenance.
ln the past, oil circuit breakers (OCBS), re-wireable fused isolators and air circuit breakers (ACBs) were the commonly used devices.
However, ACB has been acknowledged as an idea device for incomer in terms of the safety, reliability and maintenance needs of the system.
This is mainly due to its various characteristics like quick-make, quick-break stored energy type reliable mechanism, safety interlocks/ indications, ease of maintenance and its ability to withstand fault currents for a specified duration (1-3 secs) thereby allowing the feeder device to isolate the faulty branch of the network and ensuring reliable supply to healthy areas.
- Ability to achieve economy without sacriﬁcing protection and safety
- Capability to withstand abnormal currents; and
- Need for relatively less number of inter-locking indicating accessories since it covers a limited area of network.
Conventional Feeder Protection
Feeder protection covers all load centres like motor control centres, lighting switchboards and industrial load centres.
The choice of feeder protection device based on the different conventional feeder load centres are discussed below.
1. Motor Control
- Over-currents up to locked rotor condition; and
Requirements for Motor Control
|Switching normal currents||Contactors|
|Single-phasing sensing||Bi-metallic Relay|
|Over—current (up to locked rotor condition) sensing||Bi-metallic Relay|
|Switching over-currents including single-phasing current as above||Contactors|
|Logic||Timers/Auxiliary ; Contactors and other Accessories|